PELLMAX is an automatic boiler suitable for biomass burning in the form of pellets. The body is made of stainless certificate thickness of 7 mm.
plus is the construction of the boiler plate heat exchanger in the back that has a mechanism Automatic cleaning . This mechanism has two functions: it keeps clean the heat exchanger and serves as a turbulator of the exhaust gases. The boiler in this way reaches a ' constant efficiency.
The boiler is equipped with a combustion chamber extra with a grid that allows the combustion periodic wood.
Pellmax has a burner of a high quality steel, heat resistant with gliglia mobile is disabled cyclically during operation of the boiler.
The boiler is designed to allow a Easy to clean of the slag from the combustion chamber and an automatic management of the central heating pump, pump up, and circular and a Ignition System Automatic provide a simple use of the boiler.
The automatic thermal efficiency of the boiler is made possible by the electronic temperature.
The regulator controls the power of the air blower and of the gear motor, the speed of the pumps and the opening of the mixing valve.
The ' isolation of the boiler is made of rock wool covered with colored steel sheet.
The main fuel is pellets. The substitute fuel can be Coal 31.2 , dry wood - burnt on the grill.
The "kindle fire" is used to get so Automatic appropriate combustion conditions necessary to reach full capacity of combustion.
The first step is cleaning ( breath ) of the fire from the debris.
The next step is to provide a dose of fuel to create through the spiral incandiscenza , from which the fire will start the ignition process. To this end, for a certain period is actuated the loading of pellets for supplying fuel required for starting the boiler by the heater.
Here is operated Spiral and ventilator (the speed will increase gradually during power-up).
If the time should be barrier will not reveal the fire cycle will start again. After three failed tests turns on the alarm "TURN ON FIRE STOVE FAILED".